You may be wondering; why does a heating company need the services of a chimney sweep? It all has to do with how a chimney drafts. When furnaces and boilers are installed, drafting is a serious consideration. If drafting is not addressed, it could potentially lead to a very serious situation of carbon monoxide buildup that can make its way back into the basement.
When new high efficient heating systems are installed in the older homes in the Cleveland area, the inside dimension of the chimney becomes a critical factor.
When these older, larger homes were first built, they had oversized chimneys. Some of the brickwork on the exterior of these chimneys is craftsmanship at its finest. But the inside tiles of the chimney may be oversized for the new equipment. Back in the old day’s boilers and furnaces were built big with no regard for cost of fuel or efficiency. In fact, half of the heat generated by these old behemoths went up the chimney.
Nowadays, there is relatively little heat loss up a chimney. This minimal amount of exhaust can get suppressed in the larger chimney space. If that happens, it will reach dew point before it moves entirely out of the chimney. In that situation it will often condense and the resulting acidic residue will become an agent of chimney deterioration.
The solution is a flexible chimney liner that is properly sized to meet the exhaust specifications of your new heating system. This will create a draft environment that will allow for a quick and complete ventilation.
If your heating contractor isn’t discussing this potential safety issue associated with your project, then you’re not dealing with a true professional. The Hann brothers, Chris and Bill, have over 25 years of experience dealing with chimney concerns.
For the best heating sales and service in Northeast Ohio, call Verne & Ellsworth Hann; 216-932-9755. We not only take pride in our own craftsmanship we have our customer’s safety at heart.
- Alejandra, R.( Cleveland Heights, Boiler Installation, September 2018 )
Thank you for the great work!
- Linda K.( Shaker Heights, Air Conditioning Installation, September 2018 )
Your company and installers went “above and beyond” when we had a complete failure of our AC system during the hottest spell of the year. We would not hesitate to recommend to anyone who will listen!
- Thomas P.( Cleveland Heights, Boiler Installation, September 2018 )
I couldn’t have been happier with the service or final result!
- Stephanie, E.( Aurora, Furnace & Air Conditioning Installation, September 2018 )
We have used Verne & Ellsworth Hann for over 20 years. They have been consistently professional, courteous and efficient. The city inspectors in our area are sticklers for perfection, Verne & Ellsworth Hann passes with flying colors each and every inspection. Most importantly I trust their work and their staff.
- Lisa M.( Cleveland Heights, Furnace & Air Conditioning Installation, August 2018 )
We have been very happy with Verne & Ellsworth Hann! The installers were professional and efficient. I would use the company again! We already told our neighbors and they used Verne & Ellsworth Hann for a tune-up!